You should test the windings for a “short to ground” in the circuit and open or shorts in the windings. To test your motor for short to ground, you’ll need to set the multimeter to ohms and disconnect the motor from its power source. Then inspect each wire and look for infinite readings.
How do you test a 3 phase motor?
Using a multimeter, check the continuity of motor winding from phase to phase ( U to V, V to W , W to U ). Each phase to phase must have a continuity if winding is OK. If any particular phase fails the continuity test, your motor is probably burnt.
When checking a motor with a Megger the resistance from phase to ground should be?
Crank the handle for about a minute, and notice the resistance reading. Any reading above 0.5 meg-ohms is generally good.
Should a 3 phase motor have continuity to ground?
The windings (all three in a three-phase motor) should read low but not zero ohms. … It will usually be low enough (under 30 Ω) for the audible continuity indicator to sound. For proper motor operation, all windings must have megohm readings to ground, i.e. to the motor enclosure.
How do you check motor is grounded?
To test your motor for short to ground, you’ll need to set the multimeter to ohms and disconnect the motor from its power source. Then inspect each wire and look for infinite readings. Alternatively, if you get a reading of 0, you might have a cable issue.
How do you know if a motor is bad on a multimeter?
With a multimeter set to low ohms (usually 200), test between each winding terminal and the metal casing of the motor. If there is any reading on any of these then the motor is bad, do not use it. You may find that when it runs ungrounded that the casing becomes live at up to supply voltage.
How many ohms should a 3 phase motor read?
The reading should be between 0.3 to 2 ohms. If it is 0, there is a short. If it is over 2 ohms or infinite, there is an open. You can also dry the connector and retest to possibly get more accurate results.
What is the acceptable Megger reading for a motor?
A minimum value of one megohm is needed for insulation resistance. The minimum resistance of 2.4 megohms should be found in the insulation of the motor.
What is a bad Megger reading on a motor?
The measurement of insulation resistance is carried out by means of a megohmmeter – high resistance range ohmmeter.
A general rule-of-thumb is 10 Megohm or more.
|Insulation resistance value||Insulation level|
|2 Megohm or less||Bad|
How do you test a 3 phase motor inductance?
Or- If you don’t have inductance meter, the inductance of the coil can be measured by the following method.
- Measure the resistance(R) of coils(phase to phase)
- Feed AC voltage (V), 50 Hz to coils and measure the current(I)
- Calculate impedance of the coils Z=V/I.
- Calculate reactance(XL) of the coils by XL=√(Z^2-R^2)